Helping the mining industry grow in a sustainable wayLearn more
Energy education from anywhere for efficiency everywhereFree Online Courses
Your fastest way to answers!Download Now
Schneider Electric Egypt×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
TSXSCPCM4030 cable is required from TSXSCP114 PCMCIA card to the Modbus branching device TSXSCA50 for connecting other RS485 device on the Modbus Network.
In case TSXSCA50 Modbus branching device is not used, you can connect this cable directly to Modbus RS 485 device. For this you have to connect Green/White (Green wire with White Strips) and White/Green (White wire with Green strips) wires to the Tx (Transmit) and Rx (Receive) pins respectively of the RS 485 Port of the Modbus device.
Refer attachment for the pin out details of this cable for different connections.