Helping the mining industry grow in a sustainable wayLearn more
Energy education from anywhere for efficiency everywhereFree Online Courses
Your fastest way to answers!Download Now
Schneider Electric Egypt×
For the Tesys "D" Range of contactors,
- AC-1 Utlisation category: it is a general category that describes the resistive, non inductive or slightly inductive loads (mainly power factor of load 0.95 or more) and it can not be used to describe AC motors.
- AC-3 Utilisation Category: it is a general category describes all Squirrel cage motors during starting, breaking or motor running.
The Tesys "D" contactors can be used with both categories according to the application and the nature of load.
(note: the same contactor used for both categories with de-rating - there is no specific contactor reference per category).