Helping the mining industry grow in a sustainable wayLearn more
Energy education from anywhere for efficiency everywhereFree Online Courses
Your fastest way to answers!Download Now
Schneider Electric Egypt×
The conductor must be sufficiently sized and securely installed in the switchboard to accept the thermal and electrodynamic stresses of the fault current.
It must be connected to the exposed conductive parts of the switchboard.
It must be accessible to enable connections both in the factory and on site.
The cross section of the conductor as per IEC standard is SPE = √I2t / k or it can be as the manufacturer values based on the equation mentioned.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!