Helping the mining industry grow in a sustainable wayLearn more
Energy education from anywhere for efficiency everywhereFree Online Courses
Your fastest way to answers!Download Now
Schneider Electric Egypt×
It is 20%, i.e. you need to have 800A load atleast for a 4000A ACB, for the ACB to work properly (i.e. to have Micrologic display illumination).