Helping the mining industry grow in a sustainable wayLearn more
Energy education from anywhere for efficiency everywhereFree Online Courses
Your fastest way to answers!Download Now
Schneider Electric Egypt×
Please note that if the current exeeds the pick up current, the non tripping time is the time of the micrologic unit that will not respond below it
i.e , if we have a fault current value which exceeds the pick up current so the micrologic trip unit will not be able to respond in a duration less than the non tripping time.
but to be noted that in case of reflex tripping , the breaker mechanism will takes the protection action
Please check the attached PDF from the glossary of the NSX MCCB which explains this .
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!