Helping the mining industry grow in a sustainable wayLearn more
Energy education from anywhere for efficiency everywhereFree Online Courses
Your fastest way to answers!Download Now
Schneider Electric Egypt×
As per IEC60947-4-2:
· Type 1 coordination: allows the product to be damaged during short circuit condition, hence the product can be used again.
· Type 2 coordination: does not allow the product to get damaged, the product can be re-used after clearing the fault.
The maximum prospective short circuit current value is provided for the combination given, supply voltage, type of coordination (1 or 2) available in the catalog of each Soft starter/Drive range.