Helping the mining industry grow in a sustainable wayLearn more
Energy education from anywhere for efficiency everywhereFree Online Courses
Your fastest way to answers!Download Now
Schneider Electric Egypt×
1-Short terminal shields
They are used with:
a- plug-in and withdrawable versions in all connection configurations
b- fixed versions with rear connection.
2-Long terminal shields
They are used for front connection with cables or insulated bars.
They comprise two parts assembled with captive screws, forming an IP40 cover.
a- The top part is equipped with sliding grids with break marks for precise adaptation
to cables or insulated bars.
b- The rear part completely blocks off the connection zone. Partially cut squares can
be removed to adapt to all types of connection for cables with lugs or copper bars.
Long terminal shields may be mounted upstream and downstream of:
c- fixed devices
d- the base of plug-in and withdrawable versions, thus completing the insulation
provided by the mandatory short terminal shields on the device
e- the one-piece spreader for NSX100 to 250
f- the 52.5 mm spreaders for NSX400/630
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!