Helping the mining industry grow in a sustainable wayLearn more
Energy education from anywhere for efficiency everywhereFree Online Courses
Your fastest way to answers!Download Now
Schneider Electric Egypt×
The motor mechanism, MN and MX are not designed to operate at 400Hz. The solution is to supply the device through a rectifier bridge and use DC motor mechanism. To select the bridge, take into account that the absorbed power of the motor mechanism, whatever the voltage, is 500W or VA.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!