Helping the mining industry grow in a sustainable wayLearn more
Energy education from anywhere for efficiency everywhereFree Online Courses
Your fastest way to answers!Download Now
Schneider Electric Egypt×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
The selection of Direct on line starting components for a single phase motor,we consider the current of the motor mentioned on the motor nameplate,where we choose the breaker,contactor and overload,each separatly according to the current value.Please note that in this case no coordination type is guaranteed.
Regarding the overload,Standard 3 phase thermal overloads, are designed to detect a current imbalance in the 3 phase supply. As a result of this, if a single phase supply is wired such that line and neutral pass through just 2 of the 3 elements the overload can trip.
To avoid this problem when using a standard overload with a single phase motor load, the wiring through the overload must be arranged so that all three elements are in the circuit. In practice the contactor is also part of this wiring recommendation as the overload will usually be directly coupled to the contactor ;