Helping the mining industry grow in a sustainable wayLearn more
Energy education from anywhere for efficiency everywhereFree Online Courses
Your fastest way to answers!Download Now
Schneider Electric Egypt×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Yes, It is possible to Connect 3 or more motors to the same Drive ATV312, But the Selection of Drive is based uppon the total sum of the 3 Power ratings and currents.
In this case, it is necessary to provide external thermal protection for each motor using probes or thermal overload relays. If three or more motors are connected in parallel, it is advisable to install a motor choke between the drive and the motors regardless the cable lenght.
Also, For the EZC Breaker, it is not recommended for motor application.