Helping the mining industry grow in a sustainable wayLearn more
Energy education from anywhere for efficiency everywhereFree Online Courses
Your fastest way to answers!Download Now
Schneider Electric Egypt×
For the Drive, there is no such limitation on the number starts per hour, However the limitation could arise from the motor manufacturer's data, thermal class of motor,,,,etc as successive starts/hour greater than those studied by manufacturer could cause motor windings to heat thus you can use a PTC & connect to the drive
Usually the power to the drive is always on & we give start & stop command to the drive so In case you will not do this & will switch on/off the power on the drive by switching on/off the line contactor, it is recommended to wait for 60 seconds which for sure will be more than the motor supplier constraints so it will depend more on the motor manufacturer's constraints .
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!