Can Schneider Light Dimmers be controlled through Crestron Control System ?
Schneider electric uses EIB/KNX system for controlling. This system supports a group of producers, but Crestron is not in this group. Crestron use for controlling different type of protocol (Cresnet). Cresnet is 4 wire system, where two wires are for power supplying (24V) and two wire for data with it's own protocol.
KNX/EIB bus use only two wires. The data are transferred together with 29V power supply.
Therefore it is not possible to controll SE KNX dimmers with Crestron controllers