what are the proposed solutions if we need 100 A MCCB 2 pole in schneider electric offer ?
please be informed that we have 2 alternatives
1- we can use Compact NSX DC ( it works on AC/DC networks) and the reference will be as follow LV438600 , you will find attached datasheet for it and you will find also an overview for MCCB NSX DC ( which will be useful for you for more clarifications)
Note that the braking capacity of the reference LV438600 is 36 KA (differes according to network type and network voltage ) and if you require more than this you can refer to us
2- we can use MCCB NSX 100 A 3pole /2D ( which means that the 2 poles are protected but the frame size is the frame size of the 3 pole MCCB
and the reference will be as follow LV429540 and you will find the datasheet for it and the overview for the compact NSX
Note that this breaker is used for AC networks and we selected the least breaking capacity