I need a document which says that the NSX 100A/160A/250/630/800A breakers are suitable for both AC as well as DC. Because I have operational voltage of 24V DC,So will it work in DC 24V system like AC?
Page F-2 of our NSX / NW DC Catalogue shows the ratings as AC/DC for the ratings upto 160A only. We have separate offers for AC and DC and you can choose according to the application. There is no problem with 24V. The higher ratings of trip units (MP1 ,MP2 ,MP3) are only for short circuit protection and not for overload. For more details please refer the DC Catalogue.