We have Dual incomer connected to a single load. We are planning for a PLC panel ,(UPS 1 and UPS 2) there panel lamp and panel fan.For this alone we need to know weither you can use this contactor LC1D098U7 with ATS.
Thanks to note the following the contactor LC1D098U7 is suitable for AC-1 duty, Resistive load application, hence It is not recommended to use this contactor for switching FAN motor (inductive load).
You should select a contactor with AC-3 duty and suitable for Resistive and inductive load. Also you should consider the contactor current rating with AC-3 duty, since the contactor is used for DOL starting of FAN Motor.
For example you may use LC1D0935U7 (TeSys D contactor - 3P(3 NO) - AC-3 - <= 440 V 9 A - 240 V AC coil) for load current up to 9Amps.
We believe above information provided will clarify your query. Please feel free to contact us for any of further assistance.