There is a difference in power factor reading from ( varmeter controller - Varlogic - NR6 ) and the meter . Any solution ?
The power factor reading might differ according to the position of the CTs in the network. ( Are both CTs placed at the same location in the network ? ) At the same time, our Varlogic NR devices calculates and displays the Displacement Power Factor (DPF) not the true power factor.
If the other meter calculates the true power factor, and the CTs of the other meter and the Varlogic NR device are both located at the same location in the network, then there might be a difference in the values displayed by both devices.