Helping the mining industry grow in a sustainable wayLearn more
Energy education from anywhere for efficiency everywhereFree Online Courses
Your fastest way to answers!Download Now
Schneider Electric Egypt×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Circuit-breaker tripping by an MN release meets the requirements of standard IEC 60947-2.
Automatic opening of the circuit breaker is ensured when the continuous voltage supply to the release U y 0.35 x Un.
If the supply voltage is between 0.35 and 0.7 Un, opening is possible, but not
guaranteed. Above 0.7 Un, opening does not take place.